Although Raypak produces copper-finned boilers and heaters, its lineup of pool and spa products extends to both electrical and gas-fired pool heaters as well as electronic heaters. While the company’s series of commercial-grade electronic heaters — which contains models R268A and R408A, as of 2014 — cater mostly to apartment, motel and community pools, the apparatus also suit private pools, especially those in coastal regions with salty, corrosive air. In case your Raypak runs awry, the manufacturer recommends some simple troubleshooting procedures which apply to all its 2014 models.
Start With the Basics
In case your Raypak heater doesn’t fire in any respect, first make sure the unit’s time clock is set to the “On” position. A simple lack of power occasionally results in a non-firing heater, so check the fuse box for a tripped circuit breaker. Access your pool’s pump strainer basket and empty it of any debris to remedy a non-starting unit or clean your filter to troubleshoot electronic heater problems such as noisy operation, and slow or ineffective heat. Raising your pool’s water level may resolve a Raypak heater which always turns off and on.
Balance the Water
Raypak electronic heater problems such as complaining noises, reduced flow, scale formation and leaking may result from improper water chemistry. Should you encounter these problems, test and adjust your water’s pH balance as necessary. For a metallic pool with a water temperature of 68 to 88 degrees Fahrenheit, Raypak recommends a pH level of 7.3 to 7.4, total alkalinity of 120 to 150 parts per million, and calcium hardness of 200 to 300 PPM. In case you have a non-fiberglass pool with a water temperature ranging from 68 to 104 degrees, the pH should measure 7.6 to 7.8 with a total alkalinity of 80 to 120 ppm and a calcium hardness of 200 to 400 ppm. For either type of pool, Raypak suggests maximum sodium degrees of 4,500 ppm, two to three ppm of free chlorine, and a maximum total dissolved solids dimension of 3,000 ppm.
Dirty burners on the heater can lead to complications, such as soot production along with also a weak flame, which consequently causes diminished El Paso AC repair specialists power. To clean out the heater’s burners, then shut off the Raypak’s gas and power, disconnect the gas line and eliminate the unit’s front door. Unscrew the 2 screws which connect the burner tray into the heater’s frame along with the 2 screws which connect the gas valve into the coat. Slide the tray out and brush the burners clean with a wire brush. Reverse the tray removal procedure to reinstall the burner tray. Always be very cautious when dealing with gas links.
Reach Out to Raypak
As a system that caters to both residential and heavy-duty business use, lots of the components of Raypak’s electronic pool heaters call for skilled repair when they malfunction. If do-it-yourself troubleshooting processes don’t address your Raypak’s problems, call the organization or contact it via the online form at the company’s official website. When requesting service, you might require your Raypak electronic heater’s model and serial numbers, both situated on the bezel of the unit’s electronic screen.